Steel Soldiers is supported by:
If you go that way you should probably wire one side of your panel and put all your loads (breakers) on that side.Hi Guys - I've been following this and other threads regarding connecting my 002 to a small cabin I have. The cabin is already wired and has a meter base (with ground rod) that will not be connected to the power company grid for quite some time (transfer switch not presently needed). I plan on using the 120v mode for the connection to the breaker panel so I won't have to be concerned with balancing loads like I would if I used a 220v connection.
Based on what I've read so far here and in the TM, I believe that my connection should be: L-3 (hot) to lugs on breaker panel and L-1 (neutral) to neutral/ground buss on the breaker panel. My question is: Where should the Ground wire be connected - L-1, L-O, or not at all? The Change 6 wiring modification mentioned in the TM has been made. Any advice will be greatly appreciated.
I think you're mistaken about the importance of grounding. Worst case you won't be looking for a new generator. The generator might be looking for a new operator.I've called myself reading all of the threads on here about proper grounding when connecting to a residential breaker panel, but it seems they all address using a 220v connection with a ground wire connected to L-0. I can't find any information with respect to grounding using a 120v connection here or in the TM.
I guess I can try grounding to the frame of the generator and see what happens. If worse comes to worse, I'll be back to looking for another generator.
We get it, advertisements are annoying!
Sure, ad-blocking software does a great job at blocking ads, but it also blocks useful features of our website like our supporting vendors. Their ads help keep Steel Soldiers going. Please consider disabling your ad blockers for the site. Thanks!